Access panels for flues in voids
Flues in voids. People should be very aware of the extreme dangers that can occur from carbon monoxide poisoning. Many people have died from badly installed flues and from not getting regular gas safety and service checks annually.Gas Flue Inspection Specifically designed and tested to comply with the Gas Safe Regulations this panel provides a high quality robust opening solution to inspect flues installed in voids. In addition to the two sizes required by the legislation The Access Panel Company access panels for flues in voids
Nov 06, 2018 The Access Panel Company Specifically designed and tested to comply with the Gas Safe Regulations this panel provides a high quality robust opening solution to inspect flues installed in voids. Where space saving advances have allowed boilers to be fitted in wall spaces a whole flue may not be visible for inspection.
Part J Heat producing appliances. Access panels and hatches form part of a requirement to allow access to inspect concealed gas flues for heat producing appliances such as boilers, open hearths, gas cookers etc. The following information has been taken from Inspection hatches installed to provide access to an existing chimney system in a void in the majority of cases should usually have a minimum of one hour fire resistance for residential buildings with floors no higher than 18m above ground level.access panels for flues in voids Apr 03, 2017 hi guys i am just enquiring about flues in voids, i have been to a flat to do a landlords cp12 and noticed the flue is boxed in. there is only one access panel and the flue is 3 meters long, i have done a gas analyisis and that is ok and gas rate is spot on
Access panels for flues in voids free
Jul 16, 2018 Carried out a full service on a Keston c 36 last week. Boiler is in the middle of the ground floor and flues our the rear of the building via dropped ceiling in The kitchen and then eVia vertical ducting. I issued an At Risk to the customer as no access to the flue for inspection. I advised access panels were required. access panels for flues in voids May 20, 2013 The flues to these boilers were, in some cases, routed through voids in the ceiling space (and through stud walls) between properties above. This practice became progressively more popular from 2000 onwards and the vast majority of affected systems are thought to be located in new build flats and apartments completed since 2000. In order to obtain the certificate, where the flue is within a void, it will be necessary to fit access panels in order that a Gas Safe registered engineer can inspect the flue. An Estate Agent As an estate agent you can be proactive and arrange for this work to be carried out avoiding any potential issues it Flues In Voids have been serving as a leading inspection panel installer since 2010. As professionals, we're ready to tackle anything from full blocks of flats to individual properties. Our panels are designed to allow gas engineers to easily, and safely inspect boiler flues in ceilings or walls. Free No Obligation Quote Normally the inspection hatch or access panel for a boiler flue should be at least 300mm x 300mm. Boiler flue inspection hatches or access panels should be fitted within 1. 5metres of each boiler flue joint along the entire length of the void so that the engineer can examine each flue joint to ensure